The battery cabinet is a standalone independent cabinet that provides backup power at 48 volt DC nominal to a pair of triplet racks in the event of an AC outage in the data center. The batteries are a sealed 12.5 volt DC nominal, high-rate discharge type with a 10 year lifespan, commonly used in UPS systems, connected in a series of four elements for each group (called a string), for a nominal string voltage of 48VDC. There are five strings in parallel in the cabinet. The OCP Asia-Pacific chapter translated the battery cabinet specification into Japanese.
To view the CAD files, you will need to unzip them, and use a CAD viewer like the free eDrawings viewer for OS X or Windows.